GE Power Controls SOLID STATE SOFT STARTER ASTAT Plus USER MANUAL REMARKS: 1. Read this manual throughly before using the ASTAT Plus, and. General Electric/Motor Starter MPN ASTAT-QI3KDP ASTAT Plus Solid State Soft Start 50 HP Model: ASTATQI3KDP B &. Max Volts 3 Phase AC: VAC. Find great deals for GE ASTAT Plus Qi3kdp 50hp Soft Start General Electric 50 HP Starter. Shop with confidence on eBay!.
|Published (Last):||27 September 2015|
|PDF File Size:||8.94 Mb|
|ePub File Size:||1.76 Mb|
|Price:||Free* [*Free Regsitration Required]|
Bearing in mind that the direct starting torque varies between 1. Dual ramp possibility Linear speed ramp by tacho feedback also possible 3a Fast increase asatt output voltage when motor gets rated speed Current limit 4 1 to 7 In Permanent state 5 Rated voltage Override 5a Rated current 6 Energy savings. Ralentissement courant continu peut provoquer la surchauffe de moteur. In this case, linear ramp independent of a wide load range is allowed.
Traditionally in such cases other types of starting with reduced stator voltage have been resorted to. Separate motor overcurrent protection is required to be provided in accordance with the Canadian Electrical Code, Part 1. Check section for more details.
GE Astat Plus Soft start Manual
Add to watch list Remove from watch list. Chattanooga, Tennessee, United States. Adjustments are very easy to make and diverse options may be selected to have equipment capabilities suited to application needs every time. In this case the bypass is automatically done after starting.
GE ASTAT Plus Qi3kdp 50hp Soft Start General Electric 50 HP Starter
There are 5 items available. Select the lowest braking current and time. Shipping cost cannot be calculated. Learn More – opens in a new window or tab. Enabling this function the unit produces the lowest harmonic contents Description 4.
Interest will be charged to your account from the purchase date if the astwt is not paid in full within 6 months. Special financing available Select PayPal Credit at checkout to have the option to wstat over time. Full diagram 3. For additional information, see the Global Shipping Program terms and conditions – opens in a new window or tab No additional import charges on delivery Delivery: The maximum range setting is automatically calculated by the unit pls the following expression: The linear ramp function may be enabled by setting “Dxxx” to ON.
You should use an external overload protection if required by local rules or to protect the motor against current unbalance. Delay trip time The unit trips if the current increases above of the percentage set. Sets motor current limit if parameter “N” is properly adjusted.
From this it can be deduced that any start with reduced voltage reduces the torque in squared proportion to the voltage per motor phase. The actual value displayed can be stored in a temporal memory buffer by pressing key.
Any international shipping is paid in part to Pitney Bowes Inc. The vertical position is essential for proper cool air circulation – Environmental conditions are in accordance with the following ranges and maximum values: River City Industrial Home.
X – Unit frame rating F,G,H, Email to friends Share on Facebook – opens in a new window or tab Share on Twitter – opens in a new window or tab Share on Pinterest – opens in a new window or tab. Note that in general all reduced voltage starts produce a reduction in torque in squared proportion to the current in the phases of the motor not on the line and the latter in turn is reduced in linear proportion to the voltage.
Fault 1 -Latest fault- xx: You are covered by the eBay Money Back Guarantee if you receive an item that is not as described in the listing. The parameter “Sxxx” must be enabled as well.
The item may have some signs of cosmetic wear, but is fully operational and functions as intended. Set Rated Value t x x x Gr Calibration t 4 0 0 V Setting of this parameter allows better accuracy in monitoring or voltage protections.
This is usefull to stop a fan which is rotating in reverse at the starting time A tacho generator must be used as feedback.
It should be provided by a DC tacho-generator coupled to the motor. W – to stop the unit, the command will be: Semi-conductor fuses specified may not provide branch circuit protection. Supposing a cycle T, with starting time of t1, running time of T-2t1 at rated current and OFF time of t1 sec.
GE ASTAT PLUS USER MANUAL Pdf Download.
Any reduced starting voltage imposes a current limitation, and as a consequence the starting torque is also reduced, but te will always be peaks during the change from one point or state to another which can damage the machine being driven.
We generally ship orders within 1 business day of full payment. People who viewed this item also viewed. Basic diagram with DC brake injection 1. Resume making your offerif the page does not update immediately.